Question about Panasonic Heating & Cooling
The system has already determined that the thermistor is faulty so I wouldn't bother checking it as they are cheap and easy to obtain. The thermistor in question is one of two located at the right hand side of the indoor heat exchanger (the metal radiator-like assembly). One is the air temperature sensor and the other is the pipe/heat exchanger sensor. The air temp. thermistor is the one just in front of the heat exchanger held by a plastic clip. The pipe/heat exchanger sensor is the one that sits in a small metal tube near the copper pipes leading to the heat exchanger. It is usually a fairly tight fit because of a small metal insert to keep it in place. Use some small needle nose pliers on the metal insert to pull the thermistor out - NOT THE WIRES! Of course, make sure power to the A/C is completely off first.
You will probably have to replace both of the thermistors as they usually have the wires going to the same single plug on the controller board.
Posted on Apr 28, 2017
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You need four wires(two #10 and two #12) to the outdoor unit, leaving you house, and three wires(#10) coming from the breaker to tye indoor unit inside your house.
Split A/C-Cold and Hot:
You need five wires(two #10 and three #12) to the outdoor unit, leaving your house, and thee wires(#10) coming from the breaker to your indoor unit inside your house.
This ypical arrangment(all of them use three wires fro the breaker), yet there are other units which may require 6-7 wires connected to the the outdoor unit depends on the added features to the unit.
Posted on May 02, 2009
OK lets see what we can help you with here. The condensate drain is clogged. There are a couple of ways to clear this clog so lets give it a try. If you know where the drain for the a/c is located outside (usually by the outside condenser unit) it will be a pipe that is just sticking out of the side of the house, if you find it take a wet/dry vac and place it on this pipe and turn the vacuum on and make a seal with your hand this should unclog the drain. If you don't find this pipe outside the house then go to the furnace and you will see at the bottom of the furnace a pipe (PVC) white, this is the drain for the unit inside. Take the wet/dry vac and have it at the ready in the event the clog is further down the line than at the furnace itself now the fittings on this pipe should not be glued together due to the ability to access for this very purpose. Take the pipe apart at one of the fittings and place the wet/dry vac on the end of the pipe towards the furnace and using your hand make a seal and evacuate the line. Do this to both sides since you don't know where the blockage is. If you are unable to separate the pipe at any fitting you will need to cut the pipe and at the spot of the cut you will need to repair it with a sleeve. Remember that the drain pipe is plastic and is made of pvc so you can get a repair coupling from any home improvement store for this repair.
Hope this helped you some
Posted on Feb 21, 2010
the water comes from the coil, start there make sure there is no obstruction coming out to your condensate line and make sure its properly pitched.
Posted on May 22, 2010
Tips for a great answer:
Oct 13, 2017 | Panasonic Heating & Cooling
Jan 31, 2015 | Panasonic Heating & Cooling
Jan 02, 2014 | LG LS-K2430HL Heat Cool Mini Split Air...
Oct 31, 2013 | Panasonic Heating & Cooling
May 05, 2012 | Panasonic Heating & Cooling
Dec 27, 2010 | Heating & Cooling
Jan 04, 2010 | Panasonic CS-A12C Air Conditioner
Sep 19, 2009 | Heating & Cooling
Jan 14, 2009 | LG LSC183VMA Split System Air Conditioner
140 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: