Question about Heating & Cooling
You will need to do additional trouble-shooting. This could be a faulty thermostat, a broken wire at the thermostat or a problem with the furnace. At the thermostat, check that the wires are fully seated at the terminals. Make sure that the conductors haven't broken. (I've seen the wires break after they weakened.) You can try placing a jumper between the terminals for heat and ground. (For a single-phase forced air system, the Rh wire calls for heat.) If your system has a C (common) wire, make sure that the voltage is getting back to the furnace. You can try a different thermostat.
Also look at the furnace. Some systems will have an LED indicating a problem with the unit. Gas systems can have a problem with the flame. Gas or electric forced air systems could have an issue with a blower. Heat pumps can freeze up if the temperature is below their operating range.
I hope this helps. Please add a comment with the manufacturer and type of furnace (oil, gas, steam boiler) that you have if you need more ideas for trouble-shooting.
(my own gas furnace went out on Wednesday and was temporarily fixed by resetting the thermostat and using a jumper across the appropriate terminals. The flame didn't come on at 6 A.M. when the thermostat called for heat. Today, the blower completely failed and needs to be replaced. The earlier failure is likely to be related to this failing blower motor. When I followed the manual's instructions for testing the system, I got a "needs service" code. However, the unit didn't display a trouble-code before I did that test.)
Posted on Dec 17, 2016
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 07, 2018 | Heating & Cooling
Jan 04, 2016 | Heating & Cooling
Feb 09, 2015 | Heating & Cooling
Jun 08, 2017 | Heating & Cooling
Dec 07, 2010 | Honeywell Heat/Cool Thermostat
Apr 25, 2009 | Heating & Cooling
Feb 28, 2009 | Honeywell Electronic Programmable...
Jan 15, 2009 | Honeywell Electronic Programmable...
Jan 07, 2009 | Honeywell Electronic Programmable...
Dec 17, 2007 | Honeywell Power Humidifier: Furnace...
Jul 16, 2018 | Rinnai Heating & Cooling
57 people viewed this question
Usually answered in minutes!