Question about Amana Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The reset button is located behing a panel on the front of the unit that is labeled Heat Reset. If that label is gone then look around, it is a small hole, small enough for a paper clip to fit through.
That being said, I have 137 of these units in one of my hotels and have not had a single one needing to be reset. You probably are going to need a new control board kit. These can be purchased from Amana. They are $130. Make sure that you have pulled the heater coil out and inspected it first. Also, there was a recall years ago where Amana was supposed to contact and send out new voltage switches. These are the round black things that the Brown heater wires connect to on the upper and lower side of the heating coil. You should also try to replace those if you find the coil in good condition. I have had those resolve heating issues. Most of the heating issues were a result of a bad relay on the control board though.
Please remember to rate this fix.
Posted on Feb 12, 2009
A screeching or squealing noise usually comes from the fan motor. There may be an oil port and you can buy a small telescoping oil bottle at a super hardware store or an a/c supply house. Before putting in he oil, remember to TURN OFF THE POWER TO THE UNIT and only use a light squeeze on the bottle - over oiling will cause a mess inside the motor. It may be a sealed motor and no oil ports. In either case, budget for a new motor as if it's to the squealing stage, the bearings are already damaged and it's a just matter of time before before the motor bearings fail. If possible, get oil on the bearings ASAP - and use the proper lightweight oil for made for this application.
Posted on May 07, 2009
Bearing in fan going out. Let it run till it quits or call service tech to change motor. Fix cost about 250 to 300 dollars. russ
Posted on Jul 22, 2009
SOURCE: Amana PTAC
I know this is late but I had to add a solution to this problem since I had the exact same problem and was able to solve it. The probelm is not your control board. On these units, the heat pump compressor will not kick in unless the temperature you set on the control panel is within 2-1/4 degrees (or 4 degrees depending on your unit model. Otherwise, the unit locks out the compressor until the electric heat coil bring the indoor temperature up to that level - and then will switch the compressor back on for heat pump operation. So the problem is not the control panel or the compressor, it the electric heat coil. The coil has two manual limit switches on it that may be tripped and should be checked. The coil can be easily accessed by shutting down the power, removing 4 screws around the air outlet, pushing the screen up and sliding the panel out the top. The power wires can remain in place while the limit switches are reset. Hope it works.
Posted on Nov 06, 2011
Tips for a great answer:
Jun 08, 2017 | Heating & Cooling
Jun 30, 2011 | Heating & Cooling
Jan 02, 2011 | Amana PTH123B25AJ Heat Pump Air...
<a href="http://www.ultimateptac.com/ptac-faqs/">PTAC FAQs</a>
Dec 19, 2010 | Heating & Cooling
Dec 16, 2009 | Amana Refrigerators
Nov 14, 2009 | Washing Machines
May 05, 2009 | Amcor A12000E Nanomax Portable Air...
Feb 15, 2009 | Bosch Classixx WFL 2066 Front Load Washer
129 people viewed this question
Usually answered in minutes!