Question about Pentair Mastertemp 250 Natural Gas Pool Heater
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
try cycling the power to the heater itself. Check for damage (pack rats, etc..). It sounds like you may have had a direct short. It could be a board problem or a transformer problem. If you're still getting the service heater light, check to see if any diagnostic LED is illuminated behind the board.
Posted on Jan 19, 2010
This has something to do with a water temperature sensor which normally is a thermocouple.It seems that yours is reading the water temperature,sends a feedback signal to some sort of computer type controller,and when the heater output water starts getting a bit hotter than the temperature which it knows the water currently is,it's shutting down.Within thermocouples,there is a small section known as a reference temperature.That section sounds like it's gone bad because when comparing the temperatures and going above the reference,the best way to describe it is it's like popping a circuit breaker in your house,which causes shutdown,but in your house it's to prevent fire and/or save the housing wiring.In the pool heater,it's saving the water from boiling because it doesn't know when to stop.If you need more help or this is not correct,just comment back here and I will get an autolink to your post and reply ASAP.Good luck! Greg
Posted on Oct 16, 2010
This reminds me of some of the High temp sensors ive replaced. I would start with checking the pumps flow to the heater. Make sure there are no abstructions and at least 35 GPM (gallons per minute) running to the heater. If your flow is too low, you will trip the high limit sensor after a short while.
This could also mean you need to clean out the heat exchanger. When an exchanger gets dirty, it blocks the flow of water, slowing it down and "super heating" itdue to the water being in contact with the exchanger for too long. This will also trip the high limit and call for service.
If both the above items check out, contact me @ firstname.lastname@example.org and I will guide you further.
Posted on Nov 23, 2010
As a pool professional, i have yet to have this problem, and youve had this problem twice now. Have you looked inside the liquid tight flex or galvanized conduit at the wires feeding the heater? Water could be inside that line causing your power to short to ground. Id check there first.
Posted on May 21, 2014
Tips for a great answer:
May 30, 2014 | Pentair Mastertemp Heater
Jun 09, 2013 | Pentair Pool & Spa
Dec 28, 2009 | Pentair Minimax Ch 400,000 Btu Propane...
Nov 07, 2009 | Computers & Internet
Oct 28, 2009 | Pentair Mastertemp Heater
Aug 16, 2009 | Pentair Mastertemp Pool & Spa Heater Dual...
Jan 17, 2009 | Pentair Mastertemp Pool & Spa Heater Dual...
87 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: