Question about Water Water Heaters
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Probably a bad solenoid in the gas valve. Higher voltage of a new thermocouple keeps it open longer but it still fails over a period of time. Look into a new gas valve for the water heater.
Posted on Dec 17, 2009
1) Get more air to the water heater and see if problem continues.
2) Read the following pdf-s for things that might apply to your situation.
3) Read pdfs above first, and then Add a comment with missing information below, for possible do-it-yourself help.
Does this water heater have a blower?
Is gas valve electronic? Or does gas valve have a dial?
If gas valve is electronic, have you checked outlet with circuit analyzer?
Did pilot light work correctly for a while? If so how long?
Where is water heater located? Hot attic? Closet? Garage? Is area dirty and dusty? Has air intake been cleaned?
What color is pilot flame? Clear blue or yellow-or-orange?
Have you inspected inside of combustion chamber for dripping water?
Posted on Aug 29, 2011
If it is one of the new ones with the fancy gas control and the blinking light... does the light blink?? or not??
If it is blinking then the pilot should stay lit...
If it will not blink then the sensor is bad or not in the right place...
Or... the gas control is bad... this is happening alot...
If it is brand new... take it back...
Posted on Sep 05, 2011
Make sure thermocouple tip is seated inside the burner flame.
Make sure thermocouple is not overtightened. Finger-tight + 1/4 turn.
If the pilot lights, then ECO energy cut off is not tripped, but gas control valve might be bad.
Check color of pilot flame: it should be strong and clear blue.
If pilot flame is weak, or color of flame is yellow-orange: Clean pilot orifice and burner and combustion parts on yearly basis.
Clean air intake screen if applicable.
Increase air supply to water heater. Open a window and see what happens.
Check for adequate draft going up chimney using match under vent hood to see if smoke drafts immediately upwards.
Bleed air out of gas line.
Check gas pressure.
Open following links for troubleshoot resources:
Posted on Sep 21, 2011
Tips for a great answer:
Dec 18, 2014 | AO Smith A O Smith Water Heater Hot...
Sep 01, 2014 | AO Smith A O Smith Water Heater Hot...
Sep 04, 2013 | RTO W4 A.O Smith Gas Hot Water Heater...
Aug 18, 2013 | Rheem 50 Gallon FVR NATGAS Water Heater...
Dec 24, 2012 | Water Heaters
Sep 01, 2012 | Water Heaters
Dec 12, 2009 | RTO W4 A.O Smith Gas Hot Water Heater...
Aug 11, 2009 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Feb 21, 2009 | Water Heaters
Mar 10, 2018 | Water Water Heaters
42 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: