Question about Ruud Heating & Cooling
It could be flame sensor or high limit switch how long do burners run does the fan stay on while this occurs
Posted on Sep 20, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It is normal. Your house has to go down a couple more degrees because the heat pump is not working. You can solve this by rewirng you thermostat. Take off the wire that goes to Y and tape off. Then take the wires that are marked w and e or w1 and put the wires to yellow. Do not run ac with it wired like this. If you need more information please post me back
Posted on Nov 29, 2008
These new furnaces are trouble. Ive been in the htg trade for 25 yrs. The fan is running because they are now controlled by a timer instead of a temperature control. Rather than sensing a preset temperature and turning on the fan, it comes on by a preset time. Couple of things, does either of the doors have an inspection window? most newer furnaces have what is called a smart board. The board will flash a trouble code. ie: 1 long 2 short etc. #1 turn your thermostat to off, youll need 2 people for this! Go to the furnace, If it has the above mentioned inspection window ( usually about 2" round) while peering through the window have someone turn the thermostat to about 80 degrees. Let the furnace cycle and see if it flashes a code. If it does the codes are usually on the bottom door, May be on the inside. The most common cause is either a bad transformer, bad hot surface ignitor or pressure switch failure. Further questions feel free to ask. Steve
Posted on Dec 21, 2008
Look on the condensor, (outdoor unit) at the very bottom of the rear panel and you should find a red reset button. push it. If that does not solve the problem, and the outdoor unit is running (make sure both the fan AND the compressor are running) then you are looking at a low refridgerant issue and possibly dirty coils.
In that case, clean the coils and have refridgerant added.
Posted on Sep 24, 2009
I have a Silloutte II and water is dripping from the furnase. New house to us but we are having hot and humid day and need to know the maitainance that is neede to rid the water from dripping. Is there a heating unit to evaprate the water ?? please advise me on options or things to check.
Posted on Jul 29, 2010
Tips for a great answer:
Dec 20, 2013 | Ruud RGTM10ERBJS 100K BTU 95%...
Oct 19, 2013 | Heating & Cooling
Feb 23, 2013 | Ruud Rheem Rgfe09ezcms Gas Furnace
Mar 20, 2011 | Heating & Cooling
Feb 24, 2011 | Dayton Gas Furnace Heater
Mar 12, 2017 | Ruud UBHC Air Conditioner
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Dec 26, 2010 | Ruud Heating & Cooling
32 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: