Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: unit not blowing cold air
you have a slow leak in your refrigerant and need to find the leak. you will have to get an AC repairman to come to your house and check it for leaks and fix the problem.
Posted on Jul 28, 2009
If you have a heat pump probably there's a wrong connectionin the thermostat, but if is not a heat pump ,the compresor is not working or the unit leaked all the refrigerant.
Posted on Aug 30, 2009
Testimonial: "thank you, we have had a problem in the past with refrigerant leaking, was supposed to be fixed"
Make sure it is in cooling mode. Sounds like you may have a problem with the reversing valve but you would want to check the pressures in the system first and make sure the charge isn't low.
Posted on May 02, 2010
It sounds like the unit is stuck in the heat mode or the thermostat switch is still on heat. If the switch is in cool then you can go to the outside unit and locate the reversing valve. It may be stuck in the heat position. You can tap it with the handle of a screwdriver but only on the ends and very lightly because if you dent it the valve will be stuck for sure. If it shifts you will hear a loud hiss as the pressure equalizes. You could also try unplugging it from the circuit board. On some units it is energized in the cool mode and on others it is energized in the heat mode.
Posted on Jun 06, 2010
Tips for a great answer:
Dec 11, 2016 | Kitchen Ranges
Jan 11, 2014 | Majestic Fireplaces Majestic FK26 Blower...
Aug 28, 2013 | Home
Nov 21, 2017 | Heating & Cooling
Sep 21, 2011 | Heating & Cooling
Mar 07, 2011 | Heating & Cooling
Dec 02, 2010 | Heating & Cooling
Nov 08, 2010 | Heating & Cooling
Jan 07, 2010 | Napoleon 36" Zero Clearance Top/Rear Vent...
38 people viewed this question
Usually answered in minutes!