Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
the t wire is for an outdoor anticipator reset. If you dont have a terminal on your thermostat it does not have to be used. Just tape it off.
Posted on Jan 19, 2009
You may and an anolog stat and the old one was digital if so it won't work. Digital sends info to system anolog is just a set of points open or closed. Digital can carry tons of info to system like a computer. Like comparing a computer to a rock. Sorry but you need to go back to proper type stat.
Posted on Jun 30, 2009
you have to go down to your furnace and follow the thermostat wire ...it connects to a terminal strip or fan centre...the color doesn;t really matter...installers mix and match all the time....look at the furnace wiring and mark it down...Red on "R"...Green on "Y" whatever it is...and connect it accordingly upstairs...if you only have 4 thermostat wires downstairs you will need a jumper wire between RH and RC...if you have 5 wires you will see 2 wires on "R" at the furnace.,...and connect either to RH and RC at the thermostat
Posted on Nov 01, 2009
Tips for a great answer:
Aug 18, 2015 | Honeywell T87K1007 Mechanical Thermostat...
Mar 11, 2013 | Heating & Cooling
Aug 25, 2011 | Deadbolt Zurich Digital Keyless Remote...
Nov 08, 2009 | Honeywell Electronic Programmable...
Nov 01, 2009 | Honeywell Electronic Programmable...
Dec 04, 2007 | Honeywell Programmable Thermostat Heater
Sep 20, 2017 | Heating & Cooling
29 people viewed this question
Usually answered in minutes!