Question about Heating & Cooling
You could also clean the flame sensor .Look for a black sort of box or it may be round should be near the combustion fan.
Posted on Dec 14, 2016
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There is no reset button. The fault will clear itself upon cycling power to the furnace once the problem is corrected. The furnace has to establish air flow before it starts the ignition cycle. Check and make sure that your inducer motor is running during a call for heat and that the flue is free from restriction. eg. bird nests, animals, snow, ice etc.
Posted on Oct 04, 2009
where vent motor is there is usually a hose coming off which oressurizes when vent motor comes on, take hose loose **** or blow in it, take tooth pick and stick in all ports where hose connects (could be clogged) when sucking on hose you shoul hear pressure switch click each time you pull a vacumme, if fan has switch on back of fan as some Goodmans have the vent motor may need to be replaced.
Posted on Oct 28, 2009
make sure the hose from vent motor to pressure switch is not plugged, put tooth pick in both end normally the fan port is plugged.
Posted on Oct 28, 2009
SOURCE: Furnace not kicking on
Kill power to furnace and retry heat. Sometimes high winds will cause a back pressure. That will cause the switch not to work. Also is the fan coming on when it calls for heat. If not check power at the board. You have two wires that go to the draftmotor. They should have 115 volts going to them. But try killing power to unit first. rus Keep in thuch.
Posted on Dec 16, 2009
That control board is several hundred dollars. If I may make a suggestion, take a jumper and when the inducer fan starts, jump out the pressure switch. If it starts, it's not the board but a bad switch, hose or blocked exhaust vent.
Posted on Jan 15, 2010
Tips for a great answer:
Mar 29, 2017 | Bryant Heating & Cooling
Dec 14, 2016 | Heating & Cooling
Jan 23, 2016 | Heating & Cooling
Dec 23, 2012 | Heating & Cooling
Jan 31, 2011 | Heating & Cooling
Dec 21, 2010 | Ruud Central System Air Conditioner
Jan 28, 2010 | Heating & Cooling
Dec 12, 2009 | Heating & Cooling
Dec 19, 2008 | Kitchen Appliances - Others
51 people viewed this question
Usually answered in minutes!