Question about Carrier Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
YOU COULD EITHER HAVE A THERMOSTAT PROBLEM OR FAN CONTROL PROBLEM.TURN THE POWER OFF AT THE FURNACE AND TAKE THE THERMOSTAT OFF THE WALL.MAKE SURE YOU MARK THE WIRES SO YOU KNOW HOW TO HOOK IT BACK UP AGAIN.RESTORE POWER TO THE FURNACE.TOUCH THE WIRES THAT WERE HOOKED TO THE R & G TERMINALS ON THE T-STAT TOGETHER AND HOLD THEM THERE.OBSERVE THE OPERATION. WHEN YOU TAKE THEM APART DOES THE BLOWER STOP?TRY IT A FEW TIMES. IF IT CONTINUES TO START AND STOP YOU GOT A BAD T-STAT.JEFF
Posted on Dec 15, 2007
see page 2 here...the drawing section with H (hermetic compressor) F (fan) and C (common. -- http://www.docs.hvacpartners.com/idc/groups/public/documents/techlit/38en-1w.pdf
Posted on May 10, 2010
Tips for a great answer:
Dec 14, 2016 | Carrier Heating & Cooling
Jan 27, 2013 | Carrier Heating & Cooling
Jul 28, 2011 | Carrier XHD183D Air Conditioner
Jun 07, 2010 | Carrier XHD183D Air Conditioner
May 10, 2010 | Heating & Cooling
Nov 20, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 23, 2009 | Carrier XHD183D Air Conditioner
May 17, 2009 | Carrier Heating & Cooling
Dec 13, 2007 | Carrier XHD183D Air Conditioner
35 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: