Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It sounds like the blower motor has burnt up.(the one inside) The unit running for a few minutes then shutting off, is due to the high pressure/temperature safeties. When you removed the panels, did you notice any fan running?
Posted on Feb 19, 2008
does it smell like literally , dirty socks?if so it is dirty sock syndrome, a plague of heat pumps for years. if it smells like an electrical melting or burning of wires then time to call a pro.it could be a weak capacitor or a weak fan motor. if it is dirty sock syndrome then its the microbes that thrive when temps are middle temps and reproduce when temps are hot and cold in intermittent days. hot one day and cold the next equals call for cool then call for heat and hot steam from heated coils cause s bacteria to grow and microbes to spread across coil. when you switch back it causes the smell.if the coil is clean you can spend a chunk of money on sanitizers but best bet is to run it cool for hot weather and hot for cool weather. the transitional periods are what create the smell. avoid semi cool and semi hot periods. this condition is common to acs from all brands . lots of stuff on the internet about dirty sock syndrome
Posted on Nov 01, 2008
SOURCE: Blower in Attic not running
inside unit has fan control relay , either on control board or can be separate ,except for the 24 volt transformer and the t-stat the units operate separately concentrate totally on the inside unit this is where the problem lies
Posted on Nov 08, 2008
There appears to be a short in the unit. Not sure where. The power to the fan is not interrupted completly when the fan shuts down, still feeding voltage to the fan, keeping it running slow. Before checking the wiring, please turn off power first.
Posted on Nov 19, 2008
Tips for a great answer:
Oct 15, 2017 | GE Heating & Cooling
on Dec 30, 2009 | Heating & Cooling
Jun 28, 2017 | Bryant Heating & Cooling
Sep 04, 2014 | Heating & Cooling
Aug 17, 2013 | Carrier XHB123D X/Y Series Heat/Cool Air...
Feb 19, 2010 | Heating & Cooling
Oct 07, 2009 | Goodman Heating & Cooling
Aug 12, 2009 | Heating & Cooling
Apr 04, 2009 | Heating & Cooling
25 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: