Question about Heating & Cooling
You need to get in a technician to find the reason for the breaker tripping
it could be problem insulation or pest infestation causing ground leakage
otherwise you will be wasting money on the repair by replacement merry go round
Posted on Dec 10, 2016
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: breaker keeps tripping
If the breaker itself is more than 15 years old, replace it. If it continues to switch off, check the amp draw of both the inside and outside unit.
Posted on Sep 12, 2007
If your outside condenser has a locked rotor or short circuit, than the unit WILL trip the breaker - as it should. On the other hand if a breaker is tripped a few times it will have less of a capacity that the rating, (this is designed in it). You will need to determine if the unit is locked (and broken) or the breaker has become too sensitive.
Posted on Apr 22, 2008
If the fan is running and the compressor is getting hot and tripping off you may have a failed capacitor.
Posted on Jun 29, 2009
You need to borrow a clamp on style amp gauge, and check amp draw on black wire in box where hydro wires connect. (PLEASE, be careful, and if not experienced in this type of test, don't try it, due to likelihood of getting a shock. ) If it's the compressor kicking in that's causing the breaker to trip, and capacitor is good, then it's usually a problem with either low incoming (supply) 110-120 AC voltage, which will cause high amperage draw, or compressor on it's way out causing high amp draw. If it's only drawing 15-18 amps, and your tripping a 20 amp breaker, then breaker is getting weak.
Posted on Jun 05, 2010
Tips for a great answer:
Apr 04, 2017 | Heating & Cooling
Dec 31, 2012 | Reebok Exercise & Fitness
Jun 07, 2011 | Kenmore 74123 Air Conditioner
Jun 06, 2011 | Heating & Cooling
Jun 05, 2011 | Kenmore Heating & Cooling
Jun 18, 2010 | Coleman Mach 15 Air Conditioner
Jun 10, 2010 | Heating & Cooling
Apr 26, 2010 | Heritage Pool & Spa
Sep 04, 2006 | Maytag LAT2600A Top Load Washer
Jul 22, 2018 | Vulcan Heating & Cooling
29 people viewed this question
Usually answered in minutes!