Question about Dayton Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Just repaired one of these, problem was that main gas valve was not opening, valve is controlled by a vacuum switch, vacuum is created as fan blows air down tube past bent up metal flap near front bottom of heater (slight low pressure zone created). If vacuum switch is miss adjusted it will not close when fan is running and no gas flows. this is easy to check as vacuum switch also has a pressure port on it. With gas disconnected, remove bottom cover, locate vacuum switch (it has a hose clear plastic hose connected to it, in opposite corner is another hose connection, attach a length of hose to it that you can blow lightly into. With heater plugged in and no gas connected (USE CAUTION OF WIRE!!!), turn heater on you should hear after a few seconds the ignition and then a loud click as the gas valve opens, if no click blow lightly into end of your added tube, if you now hear a click the gas valve just opened. if you stop blowing you might hear the gas valve click again as it re-closes. If this is the case the vacuum switch needs to be adjusted slightly. THIS switch is hear for your safety, Adjust at your own risk!!! This can be done with a screw drive in the top, rotate screw slightly while checking if the fan alone causes enough vacuum to make the switch work. DO NOT over adjust. check safety operation before hooking up gas by placing a piece of cardboard or wood over the air intake and the exhaust to block airflow, if the air flow is blocked you should hear the gas valve drop out and reconnect as air flow is reestablished. Hope this helps
Posted on Feb 13, 2011
Tips for a great answer:
Jan 21, 2013 | Napoleon 36" Zero Clearance Top/Rear Vent...
Aug 22, 2011 | Dayton (3E227) Gas Radiator Heater
Mar 30, 2011 | Dayton (3E405) Gas Radiator Heater
Jan 17, 2011 | Dayton (3E133) InfraRed Heater
Nov 16, 2010 | Dayton Gas Furnace Heater
Dec 26, 2009 | Dayton (3E386) Heater
Oct 23, 2009 | Dayton Gas Fired Heater LP TC200VA - Heats...
Jul 11, 2009 | Dayton Gas Furnace Heater
Mar 09, 2009 | Dayton Electric Heater
May 15, 2008 | Dayton Heating & Cooling
31 people viewed this question
Usually answered in minutes!