Question about Heating & Cooling
Old, analog thermostat. Once or twice a month we have morning events in the otherwise unheated space, and need a timer, or a new, cheap, simple thermostat to turn the heat on at around 4am, and doing that by hand gets old really fast. We don't need anything with multiple program options, and really don't need anything connected to a phone.
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On your thermostat - R is the power in terminal. Y is the cooling out. W is the heating out. (G is fan out). It does not matter which wire goes to R, the other should go to W - if no heat with a call, the thermostat is bad.
Posted on Apr 17, 2009
if you cross the two wires and you see a slight spark and heat comes on, then the problem is in the thermostat, if not then problem is at furnace it self.
Posted on Apr 26, 2009
You need a specific thermostat for a Wall Furnace it is a Millivolt Thermostat and not a 24v standard thermostat....usually it will work anyway however if the powerpile (generator produces millivolts from the pilot light) is weak it may not be producing enough...or the Pilot light may be dirty and lazy...won't produce enough millivolts ...or you can have bad or dirty contacts or connections....or a combination of any of the above.....a 24v Thermostat and particularly a non-mercury thermostat has too much resistance in it for a millivolt system....as your Wall Furnace (other than the fan) runs on less than 1 volt
Posted on Oct 31, 2009
Tips for a great answer:
May 12, 2014 | Honeywell Electronic Programmable...
Aug 07, 2011 | Honeywell Water Heaters
Feb 23, 2010 | Honeywell Programmable Thermostat Heater
Feb 16, 2010 | Honeywell Electronic Programmable...
Jan 24, 2010 | Honeywell Programmable Thermostat Heater
Nov 17, 2009 | Honeywell Programmable Thermostat Heater
Oct 31, 2009 | Honeywell CT87B ROUND HEATING&COOLING...
Mar 04, 2009 | Honeywell Electronic Programmable...
Apr 24, 2018 | Heating & Cooling
66 people viewed this question
Usually answered in minutes!