Question about Computers & Internet
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If you battery packs are all at 130volts DC, then all of the packs will have become dead, and the batteries are not recoverable. Your battery DC bus voltage on a Powerware 9355 20 to 40kVA rated UPS is nominal 432 volts DC - 36 batteries in series in each string at 12 volts DC per battery. If batteries go below 10.5 volts DC each, or 378 volts DC bus voltage, no amount of charging will recover these batteries. You should not be recycling the DC battery breaker, unless you felt the battery breaker was faulty. The UPS would have given you an alarm message of either battery breaker Off, Charger Failure, or Low DC Bus Voltage long before the these batteries failed.
The battery test will not proceed if the batteries are dead.
Posted on Feb 11, 2011
Well, here's the manual and I can find no numerical alarm codes in this manual.
Posted on Feb 26, 2015
Tips for a great answer:
Feb 26, 2015 | Eaton Powerware 9355 20-30 kVA UPS...
Oct 12, 2014 | Eaton Powerware 9355 UPS System
Aug 27, 2014 | Eaton Powerware 9355 20-30 kVA UPS...
Aug 01, 2014 | Eaton Powerware 9355 UPS System
Apr 11, 2014 | Computers & Internet
Feb 18, 2013 | Eaton Powerware 9355 UPS System
May 11, 2011 | Eaton Powerware 9155 - Power Array - 10.8...
Nov 27, 2010 | Powerware Plus 36 UPS System
Feb 03, 2010 | Powerware 9355 UPS System
131 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: