Question about Aprilaire Humidifiers
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
You need to determine whether the problem is in the solenoid or in the furnace electronics. You could put a voltmeter on the solenoid connection to see if the furnace is still holding the solenoid open after the blower stops. This will tell you whether it is the solenoid or not.
Posted on Feb 19, 2007
sounds like you may have it wired to a continuous power source vs one that shuts off with the furnace. The most common wiring is red to C & white to W
Posted on Jan 13, 2010
Tips for a great answer:
Jan 13, 2013 | Aprilaire Humidifiers
Nov 15, 2012 | Aprilaire 700 Humidifier
Aug 23, 2011 | Aprilaire 550 Humidifier
Feb 20, 2011 | Aprilaire 550 Humidifier
Feb 15, 2010 | Aprilaire 700 Humidifier
Jan 28, 2009 | Aprilaire 700 Humidifier
Dec 18, 2008 | Aprilaire 600 Humidifier
Dec 02, 2008 | Aprilaire 600 Humidifier
Dec 23, 2007 | Aprilaire 550 Humidifier
Oct 30, 2007 | Aprilaire 600 Humidifier
124 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: