Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hook up o to o/b, then in the installation programming set the change over valve to energize in cool. Then hook up w to aux. Good luck.
Posted on Jan 21, 2009
The 2nd combination is correct (w/ jumper). Wire nut or tape the blue wire. The snow flake shows it's going into cooling mode after a 5 min delay. If the AC is not coming on then the problem may not be the thermostat. If you don't have 24VAC between the red wire and the blue one the problem is at the furnace or it's supply. If you do, then check for 24VAC between the blue wire and Y on the thermostat(after the 5min delay) - if it's there the thermostat is calling for cooling. To check the heat, switch the thermostat to heat mode and use the W(instead of Y) on the thermostat(after the flame stops flashing).
Posted on Apr 02, 2009
The proper way to do it would be to use a small piece of wire stripped at the ends. Then use a small amount fo solder on each end to connect RC to RH. Or use a small piece of solid(stiff) wire and strip the ends. The wrap the ends around the connector and crimp them to make contact. I would not use a paper clip. A paper clip is not designed to carry 24volt current and could melt.
Posted on Nov 02, 2009
SOURCE: Wiring problem?
Yes to everything!!
You have it figured out!!
Just make SURE that the blue unused wire cannot touch any of the other wires, it will wreck your transformer in a split second.!
I hope that this will help you to solve your problem!
Thanks for using Fixya!!
Posted on Nov 25, 2009
Tips for a great answer:
May 24, 2010 | Honeywell Electronic Programmable...
May 16, 2010 | Honeywell Programmable Thermostat Heater
Nov 14, 2009 | Honeywell Programmable Thermostat Heater
Nov 01, 2009 | Honeywell Electronic Programmable...
Oct 20, 2009 | Honeywell Focus 6300B 5-2 Days...
Sep 19, 2009 | Honeywell Focus 6300B 5-2 Days...
Jun 28, 2009 | Honeywell Programmable Thermostat Heater
Jan 05, 2009 | Honeywell Electronic Programmable...
Mar 08, 2008 | Honeywell Electronic Programmable...
52 people viewed this question
Usually answered in minutes!