Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I connected the blue wire to the R and the white wire to the W on the old thermostat and shoved the new Honeywell 5-1-1 Day programmable thermostat up the first guys *** that i ran into at Canadian Tire
Thanks for your help
Posted on Dec 29, 2008
You will have to have schematics from the old wiring diagram. Then you will have to confirm its consistency with actual old wiring before you can be sure that the wires run to the proper places on the old heater and a/c system. This sounds like a gas furnace and is simpler than a heatpump. Once you know what distinguishes the wires with the same color, you should label them and then you may call them a different color if they were wired with wrong wire colors. You may be in luck if you go to the furnace control box an look at the terminals.. They are usually labeled with a R for Red and W for white and Bl for Blue and B or Black. If you have other colors on these then it sounds that it was wired with wire spare wire by someone who knew what they were doing but neglected to leave a path for someone else follow.
You may be able to use a continuity tester of circuit tester to id these wires that are in question...
ie, once indintified, you can match with the requirements of the new stat.
Posted on Jan 13, 2009
SOURCE: honeywell thermostat
I had the same problem and decided to take a chance and call honeywell customer support. I am shocked, they solved my problem! At least in my situation we found that the blue wire ran the compressor. Instead of hooking up to "blue" on the thermostat, we hooked it up to "white." It works wonderfully now.
Posted on Apr 25, 2009
red goes to RC and RH, White goes to W, Green goes to G and Blue goes to Y. iam assuming on the old tstat that Red whent to R White went to W Green went to G and Blue went to Y
Posted on Sep 20, 2009
Testimonial: "Thanks! Worked out great!"
Tips for a great answer:
Sep 16, 2017 | Heating & Cooling
Nov 29, 2011 | Honeywell Programmable Thermostat Heater
Jun 24, 2011 | Honeywell Programmable Thermostat Heater
Mar 19, 2011 | Honeywell CT87B ROUND HEATING&COOLING...
Sep 09, 2009 | Honeywell Programmable Thermostat Heater
Aug 12, 2009 | Honeywell Electronic Programmable...
Oct 26, 2008 | Honeywell Programmable Thermostat Heater
Feb 03, 2008 | Honeywell Programmable Thermostat Heater
52 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: