Question about Coleman Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Rmove the two screws holding the blower in place and slide it out. With the power off, rotate the wheel and inspect for debris or an impingement. If everything turns easy, you have a bad motor or start capacitor. If you have rubbing, adjust the wheel. If the motor will not turn, replace it.
Posted on May 30, 2008
If you haven't already tried Coleman customer support, try Google. You can find owner's manuals for all kinds of things. good luck, John
Posted on Nov 07, 2008
SOURCE: Need wiring diagram
here would be the hook ups that are needed. at the air handler
w1/w2/aux-white (DEPENDS ON WHAT TYPE OF SYSTEM YOIU HAVE)
then these are what goes to the outside unit
o- org/or b-blue
personally contact me if yopu still have questions. thanks
Posted on Jan 12, 2009
Typically you normally will have five wires controlling your furnace and airconditioning. R Y W G C. If you get some thermostat wire. Connect them like this---- red wire will go to R(this is your 24V to thermostat)----yellow wire will go Y(Y is your cooling)----white wire will go W(W is for heating)---green wire to G(green is your fan)---black can go to C(this is your common to supply 24Vto thermostat)
Posted on Jan 19, 2009
Tips for a great answer:
Dec 22, 2015 | Coleman Heating & Cooling
Dec 07, 2013 | Coleman Heating & Cooling
Nov 26, 2013 | Coleman 7990-319p Evcon Gas Furnace...
Nov 03, 2010 | Coleman Heating & Cooling
Dec 15, 2009 | Coleman Heating & Cooling
Jun 08, 2009 | Coleman Hot Water On Demand
Dec 10, 2017 | Coleman Heating & Cooling
33 people viewed this question
Usually answered in minutes!