Question about Plumbing
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I replaced old pump w/
The water and therefore the pressure has to be going somewhere. If you are sure that there are no leaks in the house or outside, then the water is going back into the well. There is a check valve either in the suction line of the pump between the top of the well and the pump or down in the well.
If this check valve fails, it allows water to go the wrong way and back to the well. The result is that you lose pressure.
Secondly, you have to be sure that there are no air leaks between the top of the well and the inlet to the check valve. Leaks in that piping will make repriming difficult.
Write back with more and I'll try to help more.
Posted on Jan 22, 2011
You might want to make sure you have proper air volume in pressure tank.
Shut down system. Drain tank. Fill tank with air via Shrader valve on top of tank until it has a few less psi than the low cut off setting. This will ensure that the tank still has water in it with some pressure still pushing it out when the pump kicks back on.
Without that cushion of air, the pump short cycles. ie every 3 seconds.....
Posted on Aug 20, 2012
Tips for a great answer:
Apr 16, 2017 | Cars & Trucks
Apr 12, 2014 | Wayne WATER SYSTEMS SWS50-12P 1/2 HP...
Aug 12, 2012 | Plumbing
Jan 24, 2011 | Plumbing
Jan 22, 2011 | Flotec Corrosion Resistant Shallow Well...
Oct 10, 2009 | Plumbing
Sep 28, 2009 | Jet Plumbing
Jul 06, 2009 | Flotec Corrosion Resistant Shallow Well...
Apr 21, 2018 | Plumbing
Apr 19, 2018 | Plumbing
118 people viewed this question
Usually answered in minutes!