Question about Amana Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The reset button is located behing a panel on the front of the unit that is labeled Heat Reset. If that label is gone then look around, it is a small hole, small enough for a paper clip to fit through.
That being said, I have 137 of these units in one of my hotels and have not had a single one needing to be reset. You probably are going to need a new control board kit. These can be purchased from Amana. They are $130. Make sure that you have pulled the heater coil out and inspected it first. Also, there was a recall years ago where Amana was supposed to contact and send out new voltage switches. These are the round black things that the Brown heater wires connect to on the upper and lower side of the heating coil. You should also try to replace those if you find the coil in good condition. I have had those resolve heating issues. Most of the heating issues were a result of a bad relay on the control board though.
Please remember to rate this fix.
Posted on Feb 12, 2009
SOURCE: Amana PTAC
I know this is late but I had to add a solution to this problem since I had the exact same problem and was able to solve it. The probelm is not your control board. On these units, the heat pump compressor will not kick in unless the temperature you set on the control panel is within 2-1/4 degrees (or 4 degrees depending on your unit model. Otherwise, the unit locks out the compressor until the electric heat coil bring the indoor temperature up to that level - and then will switch the compressor back on for heat pump operation. So the problem is not the control panel or the compressor, it the electric heat coil. The coil has two manual limit switches on it that may be tripped and should be checked. The coil can be easily accessed by shutting down the power, removing 4 screws around the air outlet, pushing the screen up and sliding the panel out the top. The power wires can remain in place while the limit switches are reset. Hope it works.
Posted on Nov 06, 2011
Tips for a great answer:
Aug 31, 2012 | Amana PTH123B50AJ Heat Pump,12000BTU,...
Aug 27, 2012 | Heating & Cooling
Jan 02, 2011 | Amana PTH123B25AJ Heat Pump Air...
May 27, 2010 | Amana PTH123B25AJ Heat Pump Air...
Jan 28, 2010 | Heating & Cooling
Jul 23, 2009 | Amana PTH123B25AM Air Conditioner
Jul 02, 2009 | GE Zoneline AZ55H07D Air Conditioner
32 people viewed this question
Usually answered in minutes!