Question about Goodman Heating & Cooling
Here is what happens: -The blower starts and pressurizes the compartment -The igniter glows and the flame rolls out -The system runs for about 3 minutes and then the flame flickers and shuts off -The blowers stay on for a bit and the system tries to reignite the flame 3 times which triggers the system to shut off -The system LED blinks 1 time stating that it exceeded the retry/recycle limits Any help would be greatly appreciated. Thanks, Billy
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 22, 2013 | Goodman GMS90703BXA Heater
Nov 29, 2011 | Goodman Heating & Cooling
Oct 28, 2011 | Goodman Heating & Cooling
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Jan 24, 2011 | Goodman Heating & Cooling
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution:You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor. If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Nov 30, 2010 | Goodman GMS80903BNA Heater
Mar 08, 2009 | Goodman GMS90703BXA Heater
Jan 30, 2009 | Goodman GMS90703BXA Heater
Nov 23, 2008 | Goodman GMS90703BXA Heater
Nov 19, 2008 | Heating & Cooling
Oct 02, 2008 | Goodman Heating & Cooling
62 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: