Question about Heating & Cooling
First check the main panel breaker. Then check the breaker/disconnect at the condenser. If power to unit check contactor inside panel, make sure its pulled in.
Posted on Dec 03, 2016
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 24, 2016 | Mitsubishi Electric Mr Slim E12C26426...
Jun 10, 2012 | Goodman Heating & Cooling
Sep 07, 2011 | Heating & Cooling
Jul 17, 2011 | Heating & Cooling
Jun 06, 2011 | Goodman CKL36AR36 Air Conditioner
Jun 04, 2011 | Heating & Cooling
Oct 15, 2009 | Heating & Cooling
Oct 08, 2009 | Heating & Cooling
Jun 15, 2008 | Samsung AS18A6RB Air Conditioner
Oct 27, 2007 | Ruud UBHC Air Conditioner
Sep 20, 2017 | Heating & Cooling
28 people viewed this question
Usually answered in minutes!