Question about Heating & Cooling
Herd furnace kick on , and pilot kept going out . It is windy out ,and I thought that was it until I opened door ,and saw code. Furnace is a 2010 or 11 Miller. Getting cold.
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: furnace won't stay running
Furnace fails to operate.
• Integrated control module
diagnostic LED is
flashing ONE (1) flash.
• Furnace lockout due
to an excessive
number of ignition
“retries” (3 total)1.
• Failure to establish flame.
Cause may be no gas to
burners, front cover
pressure switch stuck open,
bad igniter or igniter
alignment, improper orifices,
or coated/oxidized or
improperly connected flame
• Loss of flame after establishment.
Cause may be
interrupted gas supply, lazy
burner flames (improper gas
pressure or restriction in flue
and/or combustion air
piping), front cover pressure
switch opening, or improper
induced draft blower
• Locate and correct gas
• Check front cover
operation (hose, wiring,
Correct if necessary.
• Replace or realign
• Check flame sense
signal. Sand sensor if
coated and/or oxidized.
• Check flue piping for
length, elbows, and
• Verify proper induced
draft blower performance.
Posted on Nov 25, 2008
Check the intake and exhaust plumbing for any obstructions. I had same issue, turned out to be ice in the air intake plumbing on outside of house. This may be the problem. The pressure switch can be tested by pulling hose from purge motor that goes to switch and applying a small amount of suction. The switch should make a clicking sound.
Posted on Jan 20, 2009
That control board is several hundred dollars. If I may make a suggestion, take a jumper and when the inducer fan starts, jump out the pressure switch. If it starts, it's not the board but a bad switch, hose or blocked exhaust vent.
Posted on Jan 15, 2010
Tips for a great answer:
Oct 27, 2015 | Heating & Cooling
Sep 13, 2014 | Heating & Cooling
Nov 21, 2013 | Goodman Furnace Draft Inducer Blower ...
Dec 23, 2012 | Heating & Cooling
Feb 05, 2011 | Heating & Cooling
Jan 08, 2010 | Heating & Cooling
Jan 06, 2010 | Heating & Cooling
Mar 12, 2009 | Washing Machines
Jan 09, 2009 | Coleman Propane Forced Air Heater...
Nov 08, 2008 | Cozy (W352E) Heater
29 people viewed this question
Usually answered in minutes!