Question about Leviton Hardware & Accessories
1. 3 way preset timer multiple location installation using Leviton LTB60 and vizia remote - home setup does not work since yellow/red wire on timee --where does it connect to? 2. remote connection box is a 3 way timer but has white, black and red--- how do I connect the white to and it has no yellow/red combo wire
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
HI thanks for your question. the red to red black to black white to white green goes to the fram of the dryer. thanks hope i was helpful. please rate my answer.
Posted on Oct 12, 2008
You will have to have schematics from the old wiring diagram. Then you will have to confirm its consistency with actual old wiring before you can be sure that the wires run to the proper places on the old heater and a/c system. This sounds like a gas furnace and is simpler than a heatpump. Once you know what distinguishes the wires with the same color, you should label them and then you may call them a different color if they were wired with wrong wire colors. You may be in luck if you go to the furnace control box an look at the terminals.. They are usually labeled with a R for Red and W for white and Bl for Blue and B or Black. If you have other colors on these then it sounds that it was wired with wire spare wire by someone who knew what they were doing but neglected to leave a path for someone else follow.
You may be able to use a continuity tester of circuit tester to id these wires that are in question...
ie, once indintified, you can match with the requirements of the new stat.
Posted on Jan 13, 2009
remove white switch one and connect to incoming white ground--all whites should be connected [hooked] together these are grounds-- switch 1 black from fan ,leave switch 2 red from fan ,switch 3 vanity black
Posted on Feb 22, 2010
Incoming white - outgoing white
This is the neutral, which just passes through without connecting to the switch
incoming black - switch black the hot wire provides power to the switch
switch red - outgoing red a traveler, will have power when toggle is one position
switch yellow - outgoing black
the other traveler, will have power when toggle is in the other position
incoming bare - switch green - outgoing bare the switch is grounded and it passes through
If this was helpful, please vote.
Posted on Mar 23, 2010
Switch has 2 black wires. One black is hot wire. One black is wire going to fan. Turn off power. Remove wires from switch and separate. Turn power back on. Using ordinary tester, test each black wire to bare copper ground wire. Only one of the black wires will test hot. The other black wire goes to fan.
Timer black wire connects to black hot
Timer blue wire connects to black wire going to fan
Timer white wire connects to white neutral (in absence of white neutral, connect Timer white wire to bare ground)
Timer green connects to bare ground wire
Posted on Sep 20, 2010
Tips for a great answer:
Nov 18, 2012 | Fantech FD60EM Electronic Timer Control
Aug 26, 2011 | Woods 59007 Decora Style 3015105 Minute...
Jul 18, 2011 | Leviton Vizia RF+ VRCS1-1LZ single button...
Apr 14, 2011 | Leviton Timer Switch 5-10-15-30 Minutes, 4...
Apr 04, 2011 | Leviton 6260M-T Timer Switch 10-20-30-60...
Feb 26, 2011 | Leviton 6515M-W Timer Switch, 2-5-10-15...
Jan 25, 2011 | Leviton 6230M Decora Four Preset...
Dec 26, 2010 | Leviton 6230M Decora Four Preset...
Mar 07, 2010 | Speed Leviton Vizia RF+ VRI06-1LX 600W,...
Aug 09, 2009 | Leviton Vizia Kit/Coordinating Switch -...
31 people viewed this question
Usually answered in minutes!