Question about Ruud Central System Air Conditioner
A) Ruud UPNJ-031JAZ (outside unit) trips circuit breaker (immediately) when put into heat mode.
B) Tstat set to OFF, Fan to auto; circuit breaker reset to on; outside fan & compressor seem to pulse on for one second, then off for thirty seconds, this cycle will repeat indefinitely or until circuit breaker is turned off.
C) Contactor seems to be fine (contacts move freely, holding coil pulls contacts closed when put into heat mode). This contactor has one side constant on (designed to only break circuit on one leg), other side normal spring movement.
D) Start and Run capacitors test OK (my multi-meter has capacitor test mode)
E) Heat strips come on when outside unit trips breaker
Check your wiring between the contactor and compressor for a short to ground, or check the compressor windings for short to ground.
With the Tstat off, the contactor should be open so the only way for the compressor to be trying to do anything is if the 110 volts from the unbroken side are traveling through the compressor to ground. Since 110v is not enough to run it, the overload is kicking it out, cooling off, and repeating the cycle. When you kick on the Tstat, the contactor is supplying voltage directly to ground without going through the resistence of the compressor windings and kicking the breaker.
Post back and let me know what you find.
Posted on Nov 20, 2007
Tips for a great answer:
May 16, 2014 | Goodman CLQ36AR49 Air Conditioner
Dec 05, 2013 | Air Conditioners
Nov 25, 2012 | Ruud Matching Split Air Conditioner
Mar 09, 2011 | Ruud UBHC Air Conditioner
Mar 30, 2010 | Ruud UBHC Air Conditioner
Jan 10, 2010 | Ruud Matching Split Air Conditioner
Apr 27, 2009 | Ruud Air Conditioners
Apr 10, 2007 | Ruud UBHC Air Conditioner
1,100 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: