Question about Goodman CKL60AR60 Air Conditioner
Check your refrigerant pressures at the outside unit. Should be approximately 68 low side and 225 high side. You may have a small leak in the refrigerant system.
Posted on Jul 21, 2009
Sounds like you have a restriction in your metering device, if it is a TXV it has a small screen in it that will capture debris in the system. This is a selaed system problem and unless you have proper tools will require a technician. (probably not what you wanted to heare..sorry)
Posted on Jul 19, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 27, 2012 | Heating & Cooling
Sep 30, 2010 | Fedders Heating & Cooling
Sep 22, 2010 | Beverage-Air MT17 Refrigerator Commercial
Aug 19, 2010 | Heating & Cooling
Aug 08, 2010 | Ruud Handle Air Conditioner
Jun 15, 2010 | Refrigerators
Jul 19, 2009 | Goodman CKL60AR60 Air Conditioner
Jun 20, 2009 | Heating & Cooling
Jun 12, 2009 | Honeywell Programmable Thermostat Heater
Jun 09, 2008 | Heating & Cooling
201 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: