Question about LG Heating & Cooling
Lg lsk244v-3 indoor unit starts to open, then stops and the green light flashes 6 times and nothing happens, can you help
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: LG Inverter A/C Unit LSJ092V-3
I would first check the condensate drain pipe. This can be done by blowing back into the drainpipe from outside. Not to worry it is not dirty or dangerous. Also make sure that your air filters are clean.
Posted on Mar 05, 2009
SOURCE: System will not start up.
This is a signal fault between the indoor and outdoor first make sure the dip switches are set start with the unit closest to the condensor set as unit 1 then next unit as 2 and so on the dip switches are inside the indoor unit on the pc board if you check the manual it will tell you which swithes to set, if this wasnt done when the units where installed they would have never worked i would also check the signal wiring between the wallmount and the splitter box / bc box and make sure there isnt a loose connection when you have ruled this out id say more than likely it is a faulty indoor board on the wallmounted unt
Posted on Apr 08, 2009
SOURCE: LG split (3 indoor) LMU360CE
02 Indoor In-Piping Error 2 times OFF
There is a complete guikde to problems on page 66 of users manual. If you dont have one get back to me with your email.
Posted on Aug 02, 2009
Please specify the make and model of your unit.
If this is a LG inverter model.
The six flashes of the indoor unit light indicates a CH 06 alarm.
This alarm state indicates that the indoor unit pipe temperature sensor has measured a temperature out of range or the unit is protecting itself from this low temp state. Indoor unit coil temperature to low. Should it have reached a temperature of -5°C for longer that 30sec it will switch the machine off.
It could indicate that the unit refrigerant charge is too low or the sensor has gone out of calibration.
It should measure 5kΩ @ 25°C
Posted on Mar 22, 2010
Tips for a great answer:
May 29, 2016 | Mitsubishi Heating & Cooling
May 26, 2014 | LG LMN127HVT LMN127HVT 12 000 BTU Ductless...
Jul 13, 2013 | LG Heating & Cooling
Sep 21, 2017 | Heating & Cooling
Feb 07, 2011 | Heating & Cooling
Jun 02, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Apr 17, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Mar 16, 2010 | LG Heating & Cooling
Apr 17, 2009 | Sears Craftsman LiftMaster Chamberlain...
548 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: