Question about Jandy Lite 2 Natural Gas Pilot Light Heater
My heater will not ignite. The pilot is on but when I turn on the switch nothing happens. I just bought the house last year and the previous owner said I had to turn the switch on and off rapidly several times to get it to work. Last year it worked occassionally doing this but this year I have had no luck. Any ideas?
All I can say is check for loose or corroded connections
Posted on Aug 30, 2009
The gasvalve has a pilot solenoid which is powered by in essence a thermocouple called a thermopile which converts heatfrom the pilot to to a millivolt output which is why you have to hold the pilot valve till it makes electricty. The main gas valve goes through a series of safety switches and through the thermostat so if any switch has a badoropen contact the heater will never fire find the bad part with a continuity tester and replace it.
Posted on Jul 20, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 09, 2011 | Pool & Spa
May 16, 2010 | Heating & Cooling
May 13, 2010 | Coleman 5040-751 BackHome Open Flame Patio...
Oct 07, 2009 | Intertherm Heating & Cooling
May 30, 2009 | Coleman (5040B750) Patio Heater
May 24, 2009 | Maytag Dryers
Jul 10, 2008 | Lite On Laars Lite 2 Heaters: 250,000BTU...
Sep 25, 2012 | Jandy Lite 2 Natural Gas Pilot Light...
298 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: