Question about Hayward H Series Induced Draft Abg 100,000 Heater
In a related questions answered by john224:
Actually, the clicking is likely causing the shaking. Inside the manifold of a H100 is a stainless steel diverter plate that send some of the passing water into the heat exchanger and lets the rest past and back to the pool. When it breaks, you will hear a 'clicking' noise at it rattles in the water path. When it breaks, the flow to the heat exchanger is intermittent and you will begin to boil the water, causing the shaking. This situation is dangerous, especially without a pressure relief in the heater or pipe. As long as your water chemistry is sound, Hayward will usually cover this under warranty even if the unit is over a year old. Contact them to get a factory authorized repair rep out at: http://www.haywardnet.com/locator/
What happens if this is not under warranty? Can I get the part myself and DIY it or do I have to get the whole heat exchanger? If the exchanger is the case, will it be too expensive to just replace that?
I have corrected two units with this problem. Disconnect the external piping fom the heater. When you look into the input and output pipingon the heater, you will see the loose metal plate. One unit was loose on both ends and the other on the output only. Make sure that it is clean and dry. Mix up some" JB Weld", a high temp two part epoxy and gluse the metal plates back into it correct position. After it cures (24 hours) reconnect the piping and it is good to go.
Posted on Aug 10, 2009
You can try to get a welding shop to tack it back in place (I do not remember who to credit for that but it was not my suggestion) and see if it stops.
The exchanger is expensive as a DIY part...about $350...but if that is all that is wrong it is a lot cheaper than $700+ for a whole new unit.
Posted on Jul 20, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 17, 2014 | Hayward 100,000 BTU Pool Heater H100ID1 -...
There are several things that can cause this symptom. If you have a volt/ohm meter and call the Hayward technical support at 908-355-7995
they might be able to help you figure this issue out. I hope this helps.
Please vote on this answer. Thank you.
Aug 24, 2011 | Hayward H Series Induced Draft Abg 100,000...
Jul 01, 2010 | Hayward 100,000 BTU Pool Heater H100ID1 -...
Jun 26, 2010 | Hayward H-series Electronic Gas Pool...
Jun 26, 2010 | Hayward H Series Pool & Spa Heater 400k...
May 19, 2010 | Hayward 100,000 BTU Pool Heater H100ID1 -...
Jun 17, 2009 | Hayward 100,000 Btu Heater For Ag Pool And...
May 27, 2009 | Hayward H Series Induced Draft Abg 100,000...
1,354 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: