Question about Goodman CLQ36AR49 Air Conditioner
You need to start with a basic inspection in the outside unit. For the breaker to trip immediately like that indicates a dead short. With the breaker OFF look at the internal wiring between the contactor relay and the compressor. You are looking for signs that the insulation may have been chewed by a rodent, or a wire is off of a terminal and in contact where it shouldn't be. If the wiring looks good, terminals pass tug test etc. you may have a shorted capacitor. Make sure to check the wiring for the fan too. You can disconnect the com lead for the compressor and fan one at a time to isolate the defective component if needed. Work safe! turn the breaker on for the test, and off again before you put your hand or tools back in.
Posted on Jul 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 14, 2015 | Pool & Spa
Apr 12, 2014 | Dometic Refrigerators
Apr 28, 2011 | Air-O-Swiss AOS 7135 Humidifier
Jan 07, 2011 | Water Heaters
Jun 19, 2009 | Ruud UAKA037 Air Conditioner
May 18, 2009 | Microwave Ovens
May 01, 2009 | Dometic RM2852 Refrigerator
Apr 22, 2009 | Westinghouse Dishwashers
Jul 19, 2008 | Haier Energy Star ESA3183 Air Conditioner
Mar 02, 2008 | Fahrenheat Built-In Baseboard Thermostat...
437 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: