Question about Carrier 38CKC036 Air Conditioner
The fan starts and the compressor doesn't, after time out, the unit shuts down and re-starts in about five minutes. this time only compressor starts and fan does not, you can turn fan by hand and it starts running. then the system works fine until set temp in home is reached and it fails again.
I have replaced dual run cap and also tried to beef it up by ganging two 440vac caps to meet start needs, but same condition arises.
You need a new fan motor and the correct capacitors for your sydtem I think they are 35 or 45 5 cap. Try a hard start kit on compressor. Are you sure you have the cap wired correctly?Russ
Posted on Jul 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 25, 2015 | Amana Refrigerators
Aug 01, 2011 | Heating & Cooling
Jul 31, 2011 | Refrigerators
May 08, 2011 | Goodman Heating & Cooling
Feb 12, 2010 | Ruud UBHC Air Conditioner
Jan 15, 2010 | Heating & Cooling
Sep 12, 2009 | Heating & Cooling
Jun 28, 2009 | Heating & Cooling
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
227 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: