Question about Heating & Cooling
We have central air system that turns on but does not cool
Sounds like th outdoor unit is not turning on.check to see if the motor and compressor is on.
Posted on Jul 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
A central air conditioner that runs but doesn't cool may just need to be cleaned. Plan to do this on a relatively warm day. First look for your owner's manual and, if you can find it, follow its instructions. If you can't find it, request one from the manufacturer (see Resources). To clean the filter, remove it from the furnace or air handler (it?s usually located inside or very near the air inlet side). Replace a disposable filter or clean a reusable filter according to the manufacturer?s directions. 1) Before you begin, check the thermostat to make sure it is set to "cool" rather than "heat." Then turn off the power to the unit; there is normally a shut-off or disconnect panel on the house wall next to the outdoor compressor. Otherwise, shut off the air conditioner's 240-volt circuit at the main electrical panel. 2) Rake leaves and debris away from the outdoor condenser. 3) Remove any protective grille or cover from the condenser's fins. 4) Use a soft brush to clean dirt and debris from the fins, then vacuum them with a brush attachment (be careful not to bend or damage them). If you accidentally bend fins, you can buy a comb made for straightening them at an appliance parts store. 5) Unscrew and lift the top grille off the unit, if possible. If the fan is attached to the grille, be careful not to pull any wires loose. 6) From inside the unit, hose out the fins (protect the wiring and motor with plastic). If your owner's manual calls for lubricating the motor, do that now--don't over-lubricate. 7) Then reassemble the unit. 8) To test it, turn the power on and set the thermostat to turn the unit on. Let it run for a few minutes, then feel the two pipes that connect to the condenser unit (slide any insulation back). One should feel warm, the other cool. Otherwise, call an air conditioning technician--the refrigerant may need to be recharged. NOTE: Avoid straining an air conditioner's compressor by waiting at least five minutes between turning it off at the thermostat and turning it back on. Air conditioner or heat pump still giving you trouble? To Home Problem Solver Main Page Copyright. All rights reserved. Interested in licensing this DIY Content? Related terms: what to do if, how to fix, troubleshooting, DIY, air conditioner doesn't cool, air conditioner too warm, warm air from air conditioner, air conditioner not cold enough, how to clean air conditioner, cleaning air conditioner, air conditioner cleaning
Posted on Jan 18, 2006
Change the furnace filter. Make sure you use a cheap one when air conditioning, as the better ones restrict airflow when they filter out so much stuff and then plug up, not allowing enough air to pass over the cooling coil in the furnace's air plenum. Turn the A/C off for a few hours (with only the furnace fan on if possible) to melt the ice off the cooling unit inside the furnace.
Posted on Sep 01, 2008
check t stat make sure its set up for you system some stats have to be set up for a heatpump or iits gas or electric heat
Posted on Mar 13, 2009
your indoor unit is only circulating the air in the house. for your condensing unit. check your breaker in the electric panel. your contactor or your capacitor.
Posted on Aug 09, 2009
Tips for a great answer:
May 27, 2014 | Mitsubishi MSH09TW Air Conditioner
Jan 28, 2014 | Ruud Central System Air Conditioner
Sep 28, 2010 | Ruud Heating & Cooling
Apr 05, 2010 | Ruud Central System Air Conditioner
Aug 19, 2009 | Amana Haier AP125HD Air Conditioner
Aug 09, 2009 | Carrier Heating & Cooling
Feb 25, 2009 | Heating & Cooling
Sep 01, 2008 | Carrier Heating & Cooling
47 people viewed this question
Usually answered in minutes!