Question about Plumbing
Well-Rite WR240R (well pressure tank) makes loud noise every time water flows into it-
Tank may be air bound. There is an air valve on top of tank. Take cap off and depress valve momentarily. If water comes out of valve, the bladder is torn, and new tank is needed. If no water comes out, check the pre -charge pressure of tank.
First, run water in house and take note of the on-off pressure of your pump. There should be a water pressure gauge on the water line going into the tank. Take note of the cut on pressure and cut off pressure. Most well systems typically operate at 20-40, 30-50 lbs of pressure. Next,shut off electric to pump. Drain all water from tank. Take a tire gauge and check air pressure of tank. The static or pre-charge pressure should be two lbs less than the cut-on pressure,i.e if your system operates at 30-50, then the pre-charge pressure should be at 28lbs. Adjust pressure as needed. A small air compressor is ideal to use if more pressure is needed.
Posted on Aug 16, 2009
How do I plumb in a wr240r tank
Posted on Jul 13, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2015 | Water Water Heaters
Jan 29, 2015 | Washing Machines
Jul 24, 2014 | Sta Rite Sta-Rite Max-E-Therm High...
Feb 18, 2014 | Flexcon Industries Well-Rite WR-120 Well...
Sep 24, 2011 | Braun Tassimo Espresso Machine/Coffee...
Jan 07, 2011 | Plumbing
Dec 08, 2010 | Water Heaters
Nov 14, 2010 | Sta Rite Sta-Rite Max-E-Therm High...
Oct 06, 2009 | Reliance & 40 Gal Mobile Home Water Heater...
Jun 27, 2009 | Pentair MiniMax 100 Aboveground 100,000...
2,414 people viewed this question
Usually answered in minutes!