Question about Siemens /ITE 100Amp 2-pole molded circuit breaker
After upgrading circuit breaker panel 4 months ago:
- The new Siemens Main Breaker 125 Amp gets warm and trips ocassionally (for the past 6 weeks).
- But all the other house circuit breakers Do Not trip.
- Outside meter box checked by electrical company: no problems.
How come only the Main Breaker is tripping?
Check amp draw, make sure service calculation was completed correctly, check line side and load side connection of main breaker
Posted on Dec 07, 2015
Sounds like a loose connection ,or possibly a weak main breaker.
Posted on Jul 15, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 21, 2013 | Bryant /murray Bj2200 Main Circuit Breaker...
Jan 03, 2013 | Square D Trilliant 100 Amp Circuit Breaker...
Nov 27, 2012 | Your One Source Qo Single Pole Ground...
Aug 22, 2011 | Connecticut Electric UBIF040N FPE...
Mar 05, 2011 | Siemens Murray 125 Amp Circuit Breaker...
Oct 03, 2010 | Siemens 100 Amp Main Breaker Renovation...
May 23, 2010 | Square D Qo 100 Amp Breaker Box Qo120m100...
Dec 15, 2008 | Ace Hardware Hi-Tech Circuit Detective...
Sep 03, 2007 | Heating & Cooling
1,391 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: