Question about Heating & Cooling
Indoor blower motor not responding. checked 24 volts and 120 to the fan. jump started the fan and it runs however my last idea seems to be pointing at the circuit board? help
If you have 24v between the c common terminal and g green/fan terminal on the board in the furnace and the fan does not come on, then it is the circuit board.(as long as you know the fan works)
Posted on Jul 14, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 23, 2014 | Goodman Heating & Cooling
Feb 05, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Jul 26, 2011 | Intertherm Heating & Cooling
Jun 23, 2010 | Goodman CLJ30AR32 Air Conditioner
Sep 13, 2009 | Amana Heating & Cooling
May 28, 2009 | Carrier Heating & Cooling
Apr 30, 2009 | Heating & Cooling
Apr 09, 2009 | Carrier 52PQ-515---3 Premier Series Heat...
Oct 29, 2008 | Heating & Cooling
Apr 26, 2018 | Heating & Cooling
75 people viewed this question
Usually answered in minutes!