Question about Heating & Cooling
The air conditioning portion of my day & night HVAC system (model 565BJX030000AAAA) is making a 4-5 second buzzer noise every 6 minutes. It sounds just like my dryer at the end of the cycle. It's 20 years old. What's going bad on it?
Probably the contactor, they have a coil that sometimes buzzes, after the contacts become pitted and no loger pull together like they are supposed to. It could also be a voltage problem from the transformer that is causing it, but I would bet on the contactor. Get it fixed quickly as a voltage drop across the contactor can be the demise of you compressor!
Posted on Jul 14, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 31, 2016 | Cars & Trucks
May 13, 2014 | Cars & Trucks
Feb 12, 2012 | Heating & Cooling
Feb 14, 2011 | Cell Phones
Jan 25, 2010 | Heating & Cooling
Jul 13, 2009 | Carrier Heating & Cooling
Jun 29, 2009 | Honeywell Programmable Thermostat Heater
Jun 04, 2009 | Amana ACD106R Wall/Window Air Conditioner
Jan 08, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
230 people viewed this question
Usually answered in minutes!