Question about Teledyne Laars Laars Lx Pool Heater / 400,000 Btu / Propane Gas
I have had this problem more than once over the years. The first time I found cleaning the igniter rod by lightly sanding it with an abrasive cloth or sandpaper corrected the situation. The second time was one that I really struggled with, as it would sometimes work after moving wires around. I finally found the solution had nothing to do with the heater itself, but was due to a loose ground wire in my timer box. Cleaning and reconnecting the three ground wires was all it took. I can't tell you how long it took me to finally find this solution.
Posted on Aug 04, 2013
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jul 19, 2015 | Washing Machines
Jun 05, 2015 | Pentair Mastertemp 250 Natural Gas Pool...
The high limit switch is shutting down too soon (too low of a temperature) or the fan on switch is not turning on at a high enough temperature...are they in backwards??? Even though the switches work they are not turning on and off at the right temps... so they may be out of calibration....
Feb 10, 2011 | Heating & Cooling
Jul 24, 2010 | Teledyne Laars Laars Lx Pool Heater /...
Sep 26, 2009 | Jandy Laars Lt 400,000 Btu Heater
Jun 06, 2009 | Jandy Laars Lt 250,000 Btu Heater
Mar 06, 2009 | Pentair MINIMAX NT TSI IGNITER
530 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: