Question about Ruud UBHC Air Conditioner
I assume you are referring to the outside unit, I also assume that you refer to the line side fuses. NEC codes states the the disconnect must be "within sight" of the outside unit. the fuses, (if equipped) should be in the pull disconnect located "within sight" if it was not a code installation then some dectevie work is in order, follow the line voltage conductors until you reach a junction or fuse box.
Posted on Jul 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 21, 2015 | Heating & Cooling
Jul 13, 2017 | Heating & Cooling
Feb 28, 2017 | Heating & Cooling
Jan 02, 2011 | Heating & Cooling
Jan 02, 2010 | Heating & Cooling
Jun 30, 2009 | Honeywell Electronic Programmable...
Feb 06, 2009 | Omega Trane Furnace Draft Inducer Blower...
Jan 21, 2009 | Heating & Cooling
243 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: