Question about Heating & Cooling
We installed a 13 seer condenser but the air handler is a 11 seer with a txv value but the pressurers are messed up and the copressor is over heating and shutting down
The seer rating is not what you should be concerned about. You have to be sure that the condensing unit matches the evap BTU ratings. If the evap is too small, it acts as a restriction to the system. Low back pressure, which is inadiquate return freon flow, will cause the compressor to over heat.
Hope this helps
Posted on Jul 12, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 14, 2014 | Goodman GSH130301 Heat Pump, 3 Ton, 13...
Aug 22, 2013 | Intertherm Heating & Cooling
Aug 02, 2009 | Goodman Heating & Cooling
Jul 09, 2009 | Goodman Heating & Cooling
May 27, 2009 | Heating & Cooling
May 01, 2009 | Ruud UAMB Air Conditioner
Jul 02, 2008 | Amana PTH123B25AJ Heat Pump Air...
May 06, 2008 | Heating & Cooling
74 people viewed this question
Usually answered in minutes!