Question about Heating & Cooling
Have you verified line voltage to the line side and load side of the contactor? is the contactor pulled in when there is voltage to it? if you have line power but no load pwer, and the contactor has 24v to it replace the contactor.
Posted on Jul 12, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 03, 2015 | Heating & Cooling
Dec 09, 2013 | SUBURBAN MANUFACTURING Rv Motorhome...
Mar 15, 2013 | York Furnace Draft Inducer Blower Fasco #...
Oct 08, 2012 | Coleman Mobile Modular Home Electric...
Jul 22, 2012 | AO Smith Lennox Furnace Motor P-8-6426 3/4...
Jan 25, 2010 | Aprilaire 700 Humidifier
Feb 22, 2009 | Electric Circuit Breaker Kit for Furnace
Jan 04, 2009 | Honeywell Power Humidifier: Furnace...
33 people viewed this question
Usually answered in minutes!