Question about Heating & Cooling
Need to diagnose by opening the cover to the control section and check power (24volts) where the thermostat wires connect. Check for power between terminals C and R, it should have 24 volts. Check for power between C and Y, it should be 0 volts. If there is voltage from C to Y, the thermostat is calling for cooling. If the voltage from C to Y is zero and compressor still running, the compressor contactor may still be energyzed, check for power to the coil of the compressor contactor, it should be 0 volts, if there is voltage there, the wiring has shorted and need to locate the fault. If the voltage is 0 volts, the compressor contactor is stuck or the contacts are welded together shut and needs replacing.
Some electrical skill level needed to work on live wiring, safety precautions taken. If you may, disconnect the power to the unit and inspect the compressor contactor, exercise it, the plunger should move in and out freely, a cover small contacts cover can be removed for visual inspection of the contacts, welded, burnt, stuck shut are some conditions that can be found with the compressor contactor.
Posted on Apr 30, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 25, 2017 | Cars & Trucks
Feb 13, 2015 | Heating & Cooling
Jan 11, 2011 | Northland 36SSS Side by Side Refrigerator
May 04, 2010 | Whirlpool ACE244XS Air Conditioner
Oct 06, 2009 | Ruud Heating & Cooling
Jul 19, 2009 | EMI EHW 18000 Air Conditioner
Jun 18, 2009 | Heating & Cooling
Apr 21, 2009 | Dometic Rooftop RV Air Conditioner
Jun 14, 2008 | LG Heating & Cooling
46 people viewed this question
Usually answered in minutes!