Question about Water Water Heaters
Many times the pilot needs to be pressed for a longer time until the thermocouple reaches proper temperature. Please review these steps to light your water heater:
Posted on Apr 29, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
To make a short story long (I need to include all details, sry)…
I got up one morning and realized that we did not have hot water. I re-lit the pilot light and as soon as the burner went out from heating the water up, the pilot light would go out. After reading several posts regarding this issue, it seemed apparent that the thermo-coupler was the problem. Since I am a little bit handy around the house and very tight when it comes to opening my wallet, I bought the device from Lowe’s ($8.98) that was recommended by my online advisors and after a few googles, figured out how to change it. No help. The pilot light still goes out.
I gave up and went to Home Depot to purchase and schedule the installation of a new hot water heater.
A new Direct Vent type water heater costs around $800 with an additional $450 for “special” installation. Add a few fees to that and the grand total came to about $1450.
I felt like I had no choice since my wife and 2 daughters refused to live their life without hot water and I had no clue about how to fix the dam thing.
The plumber assigned to the installation stopped by to evaluate the site conditions and quickly noted to me that the 8 year old water heater tank was in good condition and that the gas controller was probably faulty, which could be purchased online from the manufacturer. I quickly cancelled the Home Depot order and purchased the controller for about $120 after shipping and tax. Immediately after the installation it seemed that the problem had been solved. A few days later the pilot light went out.
I called the plumber and explained the situation and he recommended that I purchase another controller because the one that was shipped to me was probably bad. I searched around town and found a plumbing supply company that had the correct model in stock. Two days later the pilot light was out. I cleaned up the controller and returned it to the store and asked the plumber to please schedule a visit to repair this dam thing.
When the plumber arrived, he hooked up a gauge in several locations and confirmed that the correct amount of gas (cfm) was being delivered to the controller, pilot light and burner. He then proceeded to remove the fire box to make sure that the igniter, thermo-coupler and pilot tip were set properly. He inspected the pilot light tip and said that he found the problem. Using about a 1/64” tip drill (can be purchased at a welding supply store), he cleaned the tiny hole that releases gas to the pilot light. I felt a sigh of relief because I was certain that the problem had been solved. $65 dollars (plumber’s fee for an hour of work) and 4 days later the pilot light went out.
I called the plumber and he said that the controller that I purchased online must be bad. Too embarrassed to return to the first plumbing supply store, I found another one in a different town that had the correct model in stock. Three days after changing the controller the pilot light went out. I returned the controller and a six pack later I decided to do some extensive googling.
The key term here is “DIRECT VENT”. This seems to be a very common problem with direct vent water heaters and I was about to find out the reason for this phenomenon. I read a post by an individual who wrote that if the vent becomes detached that the inflow of air can become contaminated and extinguish the pilot light. I decided that before I spent any more money on a plumber that I was going to take the vent apart and find out what makes it tick.
My direct vent system has 2 parts to the venting, an inner pipe (3” nominal diameter) that serves as the exhaust and the outer pipe (5” nominal diameter) that serves as the internal flow of air which supplies the pilot light and burner with oxygen. On the outside of the house a vent hood helps to segregate the two by extending the exhaust about 3” beyond the intake. I looked into the hood at the end of the pipes and discovered that the internal pipe which consisted of a 2 piece slip joint had come loose from the elbow that sets on top of the water heater. This slip joint pipe was not attached at any point with screws or clamps and was loosely setting over the elbow on one end and into the hood on the other end, allowing it to detach. Apparently, when atmospheric conditions were right, the burner idled down from heating up the water and extinguished the pilot light because the intake was saturated with CO2 from the connection failure.
I purchased a section of 3” pipe that was long enough to be installed in one piece. I connected it to the elbow using a stainless steel hose clamp. I had to disassemble the pipe 3 times to make adjustments to the length and position before I got it right, but I should not have any more problems with the pilot light.
The problem here is time. It takes a lot of time to get this right. When the plumbing contractors installed this unit during the construction of the house, there was no one around to make sure that they got it right. It is probably common to use a 2 piece slip joint type connection, but I feel like it should be attached with screws or clamps. In my opinion it is not rigid enough and can detach easily, especially if it is not installed properly. A one piece connection that is attached at one end with a hose clamp and then held in place at the other end by the hood is fool proof.
Posted on Sep 27, 2009
The thermocouple has failed. It is the temp probe that goes from the pilot lite burner area to the control valve. Go to your local plumbng repair shop and buy one. Most appliance parts stores have them also. Take the old one with you and they will hook you up with an exact replacement. They are not that hard to change. Usually a nut or 2 screws in the temp bulb area at the burner end and a nut that threads into the control valve.
Make sure before you install the new one that the area where it mates to the gas valve is clean. Should be about a 20 min job including clean up with replacement parts in hand.
Posted on Jan 23, 2010
Testimonial: "exactly what I wanted yo know. thank you"
The most common reason a pilot light will not stay lit is a bad thermocouple. How old is the water heater? If the pilot light will light, but then go out when you release the safety button, that is a sure sign the thermocouple is bad. You can buy a replacement thermocouple at your local home improvement store. There is a small chance that the control valve has gone bad, but that is highly unlikely.
Posted on Feb 23, 2010
The Reliance 606 has an enclosed thermal couple. Before you try taking that assembly apart take a wire brush to the bottom opening directly under the burner. There is a metal filter on the very bottom of the water heater. It could be that the filter has gotten filled with dust or animal hair. It took a serviceman 2 days to figure this out for me. The water heater has to have good airflow through that filter to work well.
Posted on Sep 29, 2010
Tips for a great answer:
Aug 26, 2012 | Water Heaters
Aug 20, 2012 | Water Heaters
Sep 21, 2011 | Water Heaters
Aug 28, 2011 | American Standard 40 G Natural Gas Water...
Aug 16, 2011 | Rheem 50 Gallon FVR NATGAS Water Heater...
Aug 09, 2011 | Reliance Natural Gas Water Heater Control
Aug 01, 2011 | Rheem Water Heaters
Jul 30, 2011 | General Electric Water Heaters
Jul 20, 2011 | Reliance & Pilot Assembly for Natural Gas...
Dec 17, 2009 | General Electric GE SmartWater Household...
60 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: