Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
if you are getting power to the gas valve, then all of the safety switches should be closed. if you have any drain lines off of the inducer fan and at the bottom of the heat exchanger, make sure they have a trap and have water in them. the pressure switch may be the culprit.
Posted on Dec 09, 2009
Sounds like a bad fan switch. It is a small sensor attached to the heat exchanger and is designed to turn on at a specified temperature. When the unit is cold, take an Ohm meter and test for continuity across the switch. It should be open if good. If it shows a completed circuit, replace it.
Posted on Dec 27, 2009
There should be a flame sensor somewhere near the burner it will be a single wire going to a steel rod. Try cleaning this.
Posted on Dec 13, 2010
sounds like the fan motor maybe bad. take the fan door off and see if you can spin the fan. if not the motor will need to be replaced. if it does turn you will need a volt meter to test the input voltage.jumper the fan door switch and lite off the furnace.with the volt meter on the high speed wire you should see voltage in about 60/90 sec. if you have voltage once again the fan motor is bad. if no voltage your furnace is cycling off on your t-stat or your board is bad.
Posted on Mar 23, 2011
Tips for a great answer:
Dec 26, 2016 | Procom Heating & Cooling
Feb 21, 2010 | Coleman Propane Forced Air Heater...
Feb 05, 2010 | Dometic Refrigerators
Dec 09, 2009 | Coleman Propane Forced Air Heater...
Aug 09, 2009 | Hayward 100kbtu Pool Or Spa Propane Gas...
Jul 30, 2009 | Hayward H Series
Nov 02, 2008 | Coleman Heating & Cooling
Dec 09, 2007 | GE Profile JGS968 Gas Kitchen Range
124 people viewed this question
Usually answered in minutes!