Question about Miscellaneous
Check for a wire from the circuit breaker to the motors
it may be touching the motor where it goes into the case and be shorting out.
check the motors as if they are burnt out then it is the same dead short result.
Posted on Aug 03, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: breaker keeps tripping
If the breaker itself is more than 15 years old, replace it. If it continues to switch off, check the amp draw of both the inside and outside unit.
Posted on Sep 12, 2007
Check your wiring between the contactor and compressor for a short to ground, or check the compressor windings for short to ground.
With the Tstat off, the contactor should be open so the only way for the compressor to be trying to do anything is if the 110 volts from the unbroken side are traveling through the compressor to ground. Since 110v is not enough to run it, the overload is kicking it out, cooling off, and repeating the cycle. When you kick on the Tstat, the contactor is supplying voltage directly to ground without going through the resistence of the compressor windings and kicking the breaker.
Post back and let me know what you find.
Posted on Nov 20, 2007
If your outside condenser has a locked rotor or short circuit, than the unit WILL trip the breaker - as it should. On the other hand if a breaker is tripped a few times it will have less of a capacity that the rating, (this is designed in it). You will need to determine if the unit is locked (and broken) or the breaker has become too sensitive.
Posted on Apr 22, 2008
You are trying to draw too much power from the dedicated electrical line, or you may have an outlet that is needing replaced. Try to use another plug, in another room to test
Posted on Jul 21, 2008
You're unit is a 31/2 ton according to the numbers.Normally, breakers will only be in a half way posistion when tripped. Yes, under most conditions, the fuse will blow before the breaker trips. I have seen this many times, the breaker may be weak, burned, loose wires and so tighten wires, check the condition of the breaker.It sounds like the breaker even though it is 60 amps, is the problem and you should replace it with out hesitating. This will solve you're problem. When you pull the breaker out, look at the metal clips that snap in on the buss bar to see if they have been overheating.And the buss bar its self. You will know. I am sure this will take care of you're problem. Good Luck,
Posted on Dec 07, 2009
Testimonial: "Thank a lot this was very helpful"
Tips for a great answer:
Jul 01, 2014 | Pride Mobility Victory 3 Wheel Electric...
Mar 19, 2014 | Razor E300 Scooter
Feb 07, 2014 | Razor E300s Electric Scooter With Seat
Oct 28, 2013 | Hurricane Pride Pmv Mobility Scooter Candy...
Oct 13, 2011 | Razor E300 Scooter
Jan 11, 2011 | Razor E300s Electric Scooter With Seat
Dec 25, 2010 | Razor E300 Scooter
Nov 14, 2010 | Razor E300 Scooter
May 02, 2010 | Electric Mobility Mobility Electric Power...
Nov 28, 2009 | Coffee Makers & Espresso Machines
41 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: