Question about Pool & Spa
It is possible that a in line system fuse may have blown?
Also check if main power supply has been lost, normally there are two disconnects. The Main one at the main power circuit panel, that is normally a 50 amp 2pole breaker; and there is normally (by code) a 2nd auxiliary remote disconnect. Which are also 50 amp. But you could have a smaller amperage style???
I have seen many of these be a "Fusible" pull out style disconnect. You could have blown one of the fuses? Even if one blew, you will have a completely dead spa. Check this and see if you may have one?. Note these are a special type of fuse, they will be "Time Delayed or Slow Blow" system fuses. And they are about 1" in diameter and about 4" long. They can be either mounted on the pull out handle itself or inside the box pushed into their terminal clamps.
It could like one of these, click the links provided below...
Fusible AC Disconnect Switch 30 Amp
or this one, (Fusible and Non-fusible look alike)...
Non Fusible AC Disconnect Switch
The fuses behind the cover will look something like this...
Posted on Apr 28, 2015
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 09, 2013 | RCA R52WM24 52" HDTV Projection Television
Aug 04, 2012 | Balboa Instruments Duplex Digital Panel 2...
Jun 04, 2012 | Cutler Hammer CH250 2 pole 50 amp
Nov 08, 2010 | Samsung HP-T5064 50 in. Plasma HDTV
Nov 22, 2009 | Maytag Neptune FAV6800AW Top Load Washer
Nov 11, 2009 | Maytag Neptune FAV6800AW Top Load Washer
Nov 06, 2009 | Maytag Neptune FAV6800AW Top Load Washer
Jul 30, 2009 | Fisher Dishwashers
Jul 03, 2008 | Whirlpool Calypso GVW9959K Top Load Washer
Nov 26, 2007 | Frigidaire 14 Cycle Tumble Action Washer
53 people viewed this question
Usually answered in minutes!