Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Chesapeake, given your symptoms you'll be looking at installing a new Selector Switch. But, before you go there... UNPLUG THE UNIT OR SHUT OFF THE BREAKER!!! Your selector switch does two things at a time, It energizes the fan motor (which it IS doing) and energizes the compressor at the same time. The voltage to your compressor goes from the wall into the selector, out of the selector, through the temp control then to the compressor. When the temp control is satisfied, it interrupts power to the compressor. The click you hear is the temp control being NOT satisfied and trying to send power to the comp. But if there is "no power" to send (i.e., the selector switch has failed)the compressor won't know to engage. Remove the front panel and filter. Remove the control box housing. Remove the knobs from the controls. You will now see the selector switch. Remove the 2 screws that fasten it (don't remove the wire yet!) and install the new switch. Then, one wire at a time, remove the wires from the old switch and install them on the new one. ***If you have an OHM meter, check the temp control before ordering a selector because this may be the problem and NOT the selector! To do this... remove the 2 wires from the temp control, set the control to "coldest". Then with your meter, test OHM's between the terminals. If you see "zero" OHM's, it's good. If you see no change in your meter, it's bad and THIS is the source of your problem. If you don't have a meter... you can test using this procedure... cut a 6" length of wire and strip the ends to about 3/8", twist the copper ends tightly. Remove both wires from the temp control, then insert one end of your jumper wire into one terminal and the other end into the other terminal. Make sure the "jumpered" wires are away from anything metal!!! And plug the unit back in. Now turn the unit on. If the unit fires up? It's the temp control, If not? it's the selector switch. Here's a link for parts...http://www.repairclinic.com/0080.asp
Posted on Aug 09, 2007
open the service panel to check for control voltage of 24volts when tstat calling, The contactor should be pulled in, if contactor is down,and contacts appear to be clean, and the unit is still not running, it is a bad compressor. to test this unplug the black wire from the compressoror at contactor,w/ power off! Turn on power if fan works normally it's a bad compressor. However if you see a swollen split cap(5 wires to a soup can looking w/ the terminal C,F,and Comp), switch it first and start at square one.
You also need to consider the high pressure switch if its cycling on off on off.
Posted on Mar 12, 2009
If it is blinking it is in a 5 minute time delay.
It should settle to a steady snowflake after 5 minutes and come on normally.
Posted on May 25, 2009
SOURCE: My outdoor AC unit is
check power to outside unit, check if it has a fused disconnect, if you have power and no blown fuses it could be a blown capicator that starts the fan and compressor...............
Posted on May 10, 2011
Tips for a great answer:
Oct 01, 2017 | Heating & Cooling
May 21, 2017 | Honeywell Heating & Cooling
Mar 22, 2017 | Heating & Cooling
Aug 03, 2016 | White-Rodgers (Protech) White Rodgers...
Aug 03, 2011 | Honeywell Electronic Programmable...
Jul 07, 2010 | Honeywell Heat/Cool Thermostat
Sep 26, 2009 | Honeywell Electronic Programmable...
Sep 14, 2009 | Honeywell Electronic Programmable...
May 21, 2009 | Heating & Cooling
70 people viewed this question
Usually answered in minutes!