Question about Electrical Supplies
Hey, Just moved into a new apartment. Bathroom is being remodeled. Old knob and tube into a metal box feeding two switches independently ran from the box. Running one feed from the box to a plastic box in wall pigtailed to a GFIC and a switch that then runs its switch leg to a ceiling fixture. One more feed to a separate wall switch running a light over the medicine cabinet. I would love to just be able to re do all the way to the box and run a good ground so that all was known to be good but that is not an option. What would be best practice for the ground wires? Thanks much for the help!
Being as it is in the bathroom, there should be a cold-water metal pipe near. Attach a green conductor using an approved ground clamp. Run the wire to the outlet you want to ground. Attach to the box (if metal) then attach to the receptacle. If you can't get a ground installed as described, you could protect all the items (ceiling light and light over the sink) with the GFCI. All you need to do is feed the two items from the load side of the GFCI instead of the line side. This provides "people" protection as the GFCI function does not require a ground to detect the imbalance between the "hot" and the "neutral". This does not provide "equipment" protection.
Posted on Apr 29, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 03, 2013 | Home
Mar 29, 2012 | Home
Jul 07, 2011 | Moen YB2818 Eva Towel Bar Bathroom...
Oct 31, 2010 | Universal Lighting and Decor White...
Apr 27, 2010 | Hammering
Oct 29, 2009 | Broan-NuTone QTREN110 Fan
Aug 28, 2009 | 3M GFI Software GFI MailEssentials For...
May 04, 2009 | Home
Mar 22, 2009 | Your One Source Homeline Circuit Breaker
Dec 19, 2008 | Kohler Flush Actuator K 9446 [ Bathroom,...
462 people viewed this question
Usually answered in minutes!