Question about Dayton Heating & Cooling
Pilot lights and burns good set thermostat its like it kills the whole thing have bypassed the thermostat and same thing cant find a wiring diagram the fan will turn on after i hook the thermostat wires together the 2 switches in front of fan test good the ceramic i get continuity across the disk switch has 3 wires i jumped across the 2 bottom and fan comes on instantly i do have 24 volts going to the gas valve
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Sounds like one of your limit switches lost it's wire. Look for a disc like device no more bigger then a 50 piece. You will see two wires going to that and if the wire broke take off the insulation and install new plastic sheath and re-attach. Let me know it that is helpful. ken
Posted on Nov 26, 2008
DID YOU CONNECT TO TH SAME END YOU TOOK OUT WHEN PAINTING WE ARE DOWN TO THE CONNECTION @ THE HEATER MAKE SURE THE OTHER END OF TH ELEMENT IS CLOSED WITH WIRE NUTS AND TIGHT , LIKE I SAID WE ARE DOWN TO THE HEATER CONNECTIONS SO LOOK THERE
Posted on Dec 23, 2008
I am an electrician. You must measure the voltage across the black and red wires. Measuring each wire to the neutral will not cut it. If both your red and black wire are on the same phase the heater will not work.
To double check your wiring, measure the voltage across the two screws feeding your subpanel, they should be 240v or 208v depending on your power company. Then do the same at the breaker feeding your thermostat. Again it should read 240v.
If you have no potential across the screws it is possible that you installed an incorrect breaker. Not all breakers with two screws on them are 240v breakers. There is what is called a twin or split breaker that has two screws that are on the same phase. These are for wiring two 110v circuits, when you run out of spaces in the panel.
Double check everything. This is a relatively easy circuit to wire, even for homeowners. If the heater does not work them something is wrong so do not leave the circuit energized.
Posted on Mar 16, 2009
Tips for a great answer:
Jan 10, 2016 | Heating & Cooling
Dec 05, 2015 | Dayton Gas Furnace Heater
Feb 28, 2015 | Dayton Heating & Cooling
Sep 15, 2011 | Dayton Gas Furnace Heater
Dec 31, 2009 | Vanguard International VN18B Infra-Red...
Apr 07, 2009 | Dayton (4LX41) Heater
Feb 24, 2009 | Dayton (4LX41) Heater
Feb 13, 2009 | Dayton (3E386) Heater
95 people viewed this question
Usually answered in minutes!