Question about Heating & Cooling
This may need the furnace technician to repair.
I can locate the manual for your heater and the parts list but I cannot locate any reset button.
Blowers that run all the time have either a stuck fan relay or depending on age, have either a defective "fan control and limit switch" or a breaker that operates the fan. When the furnace ignites the fan waits until the air get hot before it blows. When the heat goes off, the fan continues to run until the furnace is cool.
You probably can replace the parts yourself but please make sure it runs safely. The making sure is what the furnace tech will do.
Posted on Apr 18, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You should be seeing 120 volts to the igniter. Anything less requires either a replacement of the transformer, start relay or control module.
Posted on May 30, 2008
Check your thermocoupling to make sure that it is sensing flame. You can tell if it is good or bad by the white on the tip of the flame sensor. The other problem would be a blocked or closed flue pipe. Make sure that the cap is not smashed down on the pipe on your roof
Posted on Feb 13, 2009
might be a limit switch that u reset but there might be a reason for that tripping like dirty filter or cracked heat exchanger
Posted on Jan 24, 2010
If you flip the fan to on and it doesn't run then you may have a problem with the fan motor or possibly a capacitor if it has one. I'm not familiar with the Brant heaters. I usually work on Monitor and Toyostove heaters.
Posted on Feb 12, 2010
Well mine acts up this way sometimes and I slap it on the side about half way up on the right hand side. I thinkit has a sticking relay.
Posted on Jun 10, 2010
Tips for a great answer:
Nov 07, 2015 | Coleman Heating & Cooling
Jul 12, 2015 | Coleman Heating & Cooling
Nov 28, 2013 | Heating & Cooling
Jun 17, 2017 | Coleman Heating & Cooling
Jan 07, 2011 | Water Heaters
Nov 22, 2010 | Reliance WATER HEATER CO #9-40-DKRT 40GAL...
Oct 05, 2010 | Coleman Heating & Cooling
Dec 03, 2009 | Heating & Cooling
117 people viewed this question
Usually answered in minutes!